|Place of Origin:||China|
|Certification:||CE / ISO / Explosion-proof|
|Minimum Order Quantity:||1|
|Packaging Details:||Carton / Wooden Box|
|Delivery Time:||5~8 working days|
|Payment Terms:||L/C, D/A, T/T, Western Union, MoneyGram|
|Connection:||DN15~DN40 Threaded / DN50~DN300 Flange Connection||Communication:||RS-485 / MBUS / Lora433MHZor 868MHZ / GPRS|
|Accuracy:||Class 2||Protection:||IP67 / IP68|
|Installation:||Default Is Inflow, For Return Flow Need To Indicate When Ordering||Power Supply:||High Power Lithium Battery|
|Temp. Sensor:||1.5m Standard A Pair Of PT1000 Temperature Senso|
ultrasonic btu meter,
m bus water meter
Wirless Ultrasonic Btu Meter Lora / GPRS Ultrasonic Heat Meter For Residence / Apartments / Buildings
KACISE KUHM2100 series heat meters adopt most advanced non-magnetic technology and it features elegant appearance, accurate measurement, convenient management, steady operation, strong anti-erosion, and long using life, which is secure and economic.
It is widely used in the heat system with concentrated heat supplying management, separate household data collecting management.
Varies of communication modes are optional according to the users’ need..
☆ Measure Heat.
☆ Show supply/return water temperature and differential temperature.
☆ Display pile flow measure and instantaneous flow measure.
☆ Running time display.
☆ Cool measure and display (for heat/cold Ultrasonic Heat Meter )
|Diameter||Min Flow||Quantity of Flow||Max Flow||Length|
|Measurement Accuracy||CJ128-2007<Heat Meter>Class 2|
|Connection||DN15~DN40 Threaded connection/DN50~DN300 Flange connection|
|Maximum Working Pressure(MWP)||1.6MPa|
|Flow Measuring Range||1:100|
|Temperature Sensor||1.5m standard a pair of PT1000 Temperature Sensor (cable length could be changed)|
|Data Storage||Continuous store of 18 months record|
|Power-off Protection||After power-off, meter could save all the record of before flow rate and the corresponding time, after power back, it recovery measure function automatically, and ensure the time continuation|
|Power Supply||High Power Lithium battery|
|Protection Class||IP67 (IP68 need to modified)|
|Environmental Class||Class B|
|Installation Way||Inflow or Return flow(Default is Inflow, for return flow need to indicate when ordering)|
|Installation Position||Horizontal / Vertical|
|Permanence||Service cycle≥6 years|
|Display||8-bit LCD display|
|Anti-magnetic Disturbance||When the intensity of magnetic field interference is not more than 100 ka/m, should not affect water meter measurement and remote transmission characteristics|
|Dimension (Length mm)||110||130||160||180||200|
|Max flow (m3/h)||3||5||7||12||20|
|Max flow reading||999999.99(m3)|
|Max heat reading||99999999(KW·h)|
|Battery life||>6 years ( Lithium battery)|
|Accuracy class||Class 2|
|Communication mode||Infrared interface , M-BUS/RS485|
|Press loss||≤ 0.025 Mpa ( under normal flow)|
|IP class||IP 68|
|Temperature range||(4--95) °C|
|Temperature difference range||(3--70) k|
|Starting temperature difference||0.01k|
|Temperature sensor||Pt 1000|
|Ambient temperature||+5°C -- +55°C|
|Ambient level||Level A|
|Installation||Horizontal/ vertical installation|
|Length of temperature sensor||1.5m|
|Data storage||Store historical data up to last 24 months|
Installation and Attentions
The heat meter both can be installed in Inflow pipe or Return flow pipe (factory default installed in the inflow pipe, if need to install on the return pipe, must be clearly indication before the factory during the production). When installation, should pay attention to the flow direction of medium is as the same as the arrow on the heat meter pipe body.
Special note: no matter the heat meter installed on inflow pipe or return flow pipe, the temperature sensor should be properly connected ( red label for inflow pipe, blue label for return pipe)
Instrument Common Problem
The meter cannot work normally
◇ Heating system is working or not；
◇ Globe valve is opened entirely or not；
◇ the pipe is blocked or not；
◇ the lead seal is complete or not；
◇ Battery is good or not；
◇ heat meter isn’t counting
①,heat meter reversed installation
②,transducer cables are broken
③,the filter is be blocked on heat supply pipe of in the resident room
◇ How to determine the filter whether block?
Inflow temp. is normal, return flow temp. is too low, the temp. difference of inflow and return flow is more than 10°, flow rate is too low(m3/h), or now flow rate, usually the filter is blockage, or user does not use.
Solution:Close the valve (inflow and return flow valve), remove the filter, to observe whether filter is black, clean filter and inside of it, then install the filter, open pipe valves, wait 3 mins to check whether the flow rate and temp. is normal.
◇ Heat meter data abnormal or jumping
①,Installation position is not correct, down water level
②,Front and back straight pipes are too short, bend is too big, front pipe diameter is
◇ Heat meter has flow quantity, no heat, or heat is very big
①,Without heat is usually reversed installation of inflow and return flow temp. sensors
②,Heat is very big, because the temp. sensor measure temp. incorrectly, temp. difference is very big.
◇ Heat meter abnormal temp., or the temp. is 0
①,the temp. sensor cable is broken
②,Temp. sensor stainless steel casing is broken.
Contact Person: Sales
Address: i City, No11, TangYan South road, Yanta District, Xi'an,Shaanxi,China.
Factory Address:i City, No11, TangYan South road, Yanta District, Xi'an,Shaanxi,China.